Victron Multiplus II 12V, 2.4kW inverter/charger for use off grid on or on grid with 120A AC - DC Charger
The MultiPlus-II combines the functions of the MultiPlus and the MultiGrid.
It has all the features of the MultiPlus, plus an external current transformer option to implement PowerControl and PowerAssist and to optimize self-consumption with external current sensing (max. 32A). It also has all the features of the MultiGrid with built-in anti-islanding and an increasingly long list of country approvals.
The MultiPlus-II will prevent overload of a limited AC source, such as a generator or shore power connection. First, battery charging will automatically be reduced when otherwise an overload would occur. The second level will boost the output of a generator or shore side supply with power taken from the battery.
ESS: Energy Storage Systems
The MultiPlus-II is the key component in a Victron ESS system, providing the flexibility to combine with MPPT Solar Chargers or Grid-tie PV Inverters. For examples and more detailed information see the ESS (Energy Storage System) manual.
Uninterrupted AC power (UPS function)
In the event of a grid failure, or when shore or generator power is disconnected, the inverter within the Multi is automatically activated and takes over the supply to the connected loads. This happens so fast (less than 20 milliseconds) that computers and other electronic equipment will continue to operate without disruption.
Remote Monitoring and Control
Monitor and control your Multi and system or systems' locally (LAN) or remotely via the internet from anywhere in the world, using the free VRM app and free VRM portal website. Access can be from a phone, tablet, laptop or PC for multiple operating systems. There is no end to the level of control, via the required Color Control GX or Venus GX, from adjusting your Multi to auto starting a back generator and more...
0 - 5m = 2 x 50mm square on the positive and 2 x 50mm square for the negative battery connection cables.
5 - 10m = 2 x 70mm square on the positive and 2 x 70mm square for the negative battery connection cables.
M8 bolts on unit for cable connection.